|Place of Origin:||China|
|Certification:||CE / ISO / FDA|
|Minimum Order Quantity:||1|
|Packaging Details:||Bubble Wrap/ Wooden Case|
|Delivery Time:||5-8 work days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 Unit per Month|
|Name:||Softened Water Equipment||Feed Water Pressure:||0.2MPa|
|Raw Water Hardness:||8mmol/L Max||Salt Consumption:||160-250 G/Mol (According To Water Conditions)|
|Effluent Residual Hardness:||0.03mmol/L Max||Working Temperature:||40-60°C|
|Control Method:||Time-Periodic Model||HS Code:||8421219990|
commercial reverse osmosis water filtration system,
commercial ro filter Boiler,
commercial reverse osmosis water system
Demineralized water equipment is to remove inorganic salts such as calcium and magnesium from common water (after heating daily water, the product will precipitate substances, commonly known as scale). Softened water is called reducing the hardness of water in the industry, so softened water equipment can also be called: hard water softening treatment equipment, water softener and water softener.
Automatic softener water machine adopts the technology that using ion exchange to remove impurity such as calcium magnesium from water to make the water soften.The raw water can exchange the hardness composition of Ca2+ and Mg2+ with Na+ by sodium ion exchange resin, so that to absorb Ca2+ and Mg2+ ions and achieve water softening.
Widely used in steam generator, pulsating vacuum sterilizer, heat exchanger, central air conditioning cooling cycle's water softening.It can also be used in industrial, civil, food, pharmaceutical and electronic industries' water softening.
1> Automatic operations and procedures.
2> Stable operation ensureas softening effect.
3> Low cost, energy saving.
4> Compact structure, small standing area.
5> Directly connected with the tap water for deep softening.
6> Simple installation,it can be used when equipped with water and electricity.
|Model||Water output (L/H)||Resin content (kg)||Model and qty
|Salt box size and qty (f×H)||GPM||Working pressure range
|Water inlet pressure (Mpa)||0.2-0.4||0.3 is best|
|Salt consumption (g/mol)||160-250 max|
|Raw water hardness||8||Below 8 is better|
|Effluent residual hardness (mmol/L)||0.03 max|
|Water temperature (C)||2-38|
|Water consumption rate(L/H)||2%max of output||According to the using type.|
|Water output (L/H)||100-200|
|Resin type||001*7 type of strong acid cation exchange resin|
|The weight(kg)||35||According to the using type.|
|Size (mm)||480X280X1150||According to the using type.|
|Area (m2)||0.2||According to the using type.|